|Place of Origin:||XI'AN CHINA|
|Brand Name:||HERONG ELECTRIC|
|Minimum Order Quantity:||1PC|
|Packaging Details:||Export standard packing|
|Delivery Time:||30 work days|
|Payment Terms:||L/C, T/T, D/A, D/P, Western Union, MoneyGram|
|Rated Voltage:||11.55KV||Rated Capacity:||100kvar|
|Rated Current:||8.66A||Rated Capacitance:||2.39uF|
|Rated Frequency:||50Hz||Internal Fuse:||Yes|
|Insulation Level:||50/125KV||Number Of Phases:||Single-phase|
|Capacitance Deviation:||-3%～+3%||Package:||Export Standard Packing|
100 Kvar High Voltage Capacitor Bank,
11.55KV High Voltage Capacitor Bank,
50Hz 100 Kvar Capacitor Bank
50Hz 11.55KV 100kvar High Voltage Capacitor Bank For Improving Power Factor
1. Overview of 11.55 KV 100kVar High Voltage Shunt Capacitor
High voltage shunt capacitor (Power capacitor) is mainly used in the A.C,Power system with 50Hz or 60Hz to improve power factor, reduce reactive power loss, mend voltage quality, plenitude elaborate generate power' equipment and supply power equipment efficiency, it is national recommend save power products.
2. Function of 11.55 KV 100kVar High Voltage Shunt Capacitor
High voltage parallel capacitor is composed mainly of the packet, shell and insulation porcelain, the packet is connected in a particular way by dozens of components, separated by insulation and wrapped. The shell is welded with thin steel plate (or stainless steel plate),the two sides of the wall have the bracket for welding and installing. The lid of box is covered with (or embedded pressure assembly) line casing,components are made of polypropylene film and aluminum foil,and the capacitor is filled with excellent electrical insulation liquid impregnant.
|Rated Capacity||100 kvar|
|Number of phases||Single-phase|
|Loss tangent value (tanδ)||≤0.0003|
|Discharge resistance||The capacitor is equipped with a discharging resistor. After being disconnected from the grid, the voltage on the terminal can drop below 50V within 5 minutes|
3. Main features of 11.55 KV 100kVar High Voltage Shunt Capacitor
1. The horizontal separated plate shall not be mounted, or it may block air flow. Outlet for cooling air shall be mounted on the top of each group of capacitors.
2. Before capacitors mounted on support, it shall allocate the capacitance, make phase capacitance to be balanced (balance rate 5%)
3. Wire connection for capacitors shall use soft conductor. The side of capacitor with nameplate shall face outside, convenient for inspection.
4. When rated voltage of capacitor is equal to the system, the capacitor can be directly mounted on steel support, and the shell of capacitor is earthed and well connected. If the rated voltage of single phase capacitor less than system voltage, please utilize star connection for these capacitors, at this case the shells of series connected capacitors shall absolutely isolated from earth, its insulation level not less than rated voltage of the system.
4. Applicable standard of 11.55 KV 100kVar High Voltage Shunt Capacitor
IEC60871 and equivalent standard
5. Working conditions of 11.55 KV 100kVar High Voltage Shunt Capacitor
1, Altitude:Less 1000m;Ambicnt Temperature:-40℃ to 40℃.
2, No violcnt mcchanical vibration, no harmful gas and vapor ,no electric,and cxplosive dust in location.
3‚ Power capacitor will work in the good ventilate condition, it would not permit to work in sealing and no ventilate condition.
4‚ Power capacitor connection wire should take soft conductive wire, the whole circuit connect well.