|Place of Origin:||XI'AN CHINA|
|Brand Name:||HERONG ELECTRIC|
|Minimum Order Quantity:||1PC|
|Packaging Details:||Export standard packing|
|Delivery Time:||30 work days|
|Payment Terms:||L/C, T/T, D/A, D/P, Western Union, MoneyGram|
|Rated Voltage:||9.1KV||Rated Capacity:||276kvar|
|Rated Current:||30.33A||Rated Capacitance:||10.61uF|
|Rated Frequency:||50Hz||Internal Fuse:||Yes|
|Insulation Level:||50/125KV||Number Of Phases:||Single-phase|
|Capacitance Deviation:||-3%～+3%||Package:||Export Standard Packing|
276kvar HV Capacitor Bank,
50Hz AC Power System Capacitor Bank,
9.1KV Electrical Capacitor Bank
9.1KV 276 kVar Capacitor Bank High Voltage 50Hz Rated Frequency
1. Overview of 9.1KV 276kVar High Voltage Shunt Capacitor
High voltage shunt capacitor (Power capacitor) is mainly used in the A.C,Power system with 50Hz or 60Hz to improve power factor, reduce reactive power loss, mend voltage quality, plenitude elaborate generate power' equipment and supply power equipment efficiency, it is national recommend save power products.
2. Function of 9.1KV 276kVar High Voltage Shunt Capacitor
Medium voltage shunt capacitor/High voltage shunt capacitor are suitable for 50Hz or 60Hz AC power systems to improve the power factor of the power system, reduce line losses, improve the quality of the power supply voltage, and increase the active output of the transformer.
|Rated Capacity||276 kvar|
|Number of phases||Single-phase|
|Loss tangent value (tanδ)||≤0.0003|
|Discharge resistance||The capacitor is equipped with a discharging resistor. After being disconnected from the grid, the voltage on the terminal can drop below 50V within 5 minutes|
3. Main features of 9.1KV 276kVar High Voltage Shunt Capacitor
1. All these series capacitors serve for common ambient conditions, standard category for capacitor covers -40/A,-25/A,-5/A,-5/C, working altitude not more than 1000m
2. The capacitors shall be mounted in the place where there shall comply with the requirement of clause 5.1, the capacitor for indoor use shall be mounted on the place where there has no corrosive steam and gas, and snow, rain, dust can't be accessible, and well ventilated.
3. The capacitor can be mounted on steel support, layout not more than 3 layers, each layer not more than two rows. In order to get good ventilating, the clearance between capacitors in each layer shall not less than 200mm, outdoor capacitor shall have 300mm at least, and the top of the capacitor shall have 1000mm away from house roof at least.
4. The horizontal separated plate shall not be mounted, or it may block air flow. Outlet for cooling air shall be mounted on the top of each group of capacitors.
4. Applicable standard of 9.1KV 276kVar High Voltage Shunt Capacitor
IEC60871 and equivalent standard